How to install
wood floors on underfloor heating
Underfloor heating is ideal for our wood floors. Here you will find advice for choosing underfloor heating for your wood floor.
Underfloor heating is ideal for wood floors
Today, wooden floors and underfloor heating are often combined and work well together. Both electrical and hot-water underfloor heating can be used with Kährs hardwood floors. It is, however, very important to follow both our specially designed installation instructions, as well as the instructions and recommendations given by the supplier of the underfloor heating system. If properly installed, you will achieve a beautiful and long-lasting wood floor with the increased comfort of pleasant warmth. Here you will find instructions and advices on what to consider when choosing underfloor heating for your hardwood floor.
Temperature of the surface
The surface temperature of the floor must never exceed 81°F (27°C). This also applies to areas next to radiators and elements, under furniture and carpets, etc. With good furnishing and without too many carpets, or carpets that are too thick, it is reasonable to achieve a temperature of 73°F (23°C) over the entire floor area, for a room temperature of around 69°F (21°C). Of course, this is assuming that the room requires a normal amount of heating. This means that your sealing, insulation, windows, etc., must be of regulation standard quality. Extra precautions should be taken to ensure the temperature at the feeding of the hot water never exceeds the maximum level, and that installation instructions provided by the supplier of the heating system are followed correctly.
Susceptible to moisture
Floors with underfloor heating are more susceptible to moisture than those without. This is because the difference in moisture content between the driest and dampest parts of the floor will increase over time. Underfloor heating can cause extensive drying, which makes the wood contract and shrink. In a cold, dry climate, you can expect to see gaps between strips and slightly concave boards from time to time. We recommend Kährs Original 15 mm flooring or Kährs Linnea 7 mm with Woodloc® or Woodloc® 5S joints for floors with underfloor heating. Both Kährs Original and Kährs Linnea reduce the risk of gaps forming.
It is worth bearing in mind that parquet flooring made from Beech and hard Maple expands and contracts more than other wood species and is therefore not recommended for use with underfloor heating.
Installing over underfloor heating
Your wood floor must be laid close to the subfloor and without an air gap, as air gaps can cause the wood to dry out very quickly.
When laying a floor over underfloor heating loops, the working temperature should be at least 64°F (18°C). This is applicable to boards, subfloors and room temperature. The relative humidity (RH) of the air must be between 30 and 60% before, during and after laying the floor.
Special requirements when installing underfloor heating
- The floor construction must have a heat-distributing layer that gives an even temperature over the entire surface of the floor area, in order to prevent high temperatures in certain spots.
- It must be possible to control and limit the surface temperature with a high degree of accuracy.
- The entire floor area must be heated. However, this does not apply to comfort heating systems, which complement normal heating. In this case, the temperature should be considerably lower than the permitted 27°C floor surface.
- The laid floor - including the intermediate layer - must have a low thermal resistance.
- A vapour barrier must be built into the floor construction, positioned as close as possible to the wood floor. It is particularly important to have the vapour barrier near to the wood floor if the joists are thick or heavy. Under no circumstances may the vapour barrier be placed on the opposite side of the joists.